Slim Fire Sleeves prevent the spread of fire where plastic pipes penetrate fire compartment walls. They are specifically designed to be slim for applications where there is limited space around the duct.
Features & Benefits
- CE Marked
- Tested to BSEN 1366-3: 2009
- Tested with Uncapped/Uncapped (U/U) duct configurations as required for ventilation ducts
- Up to 2 hour fire rating
- Very slim-line (saves ceiling space)
- Suitable for masonry walls or plasterboard partitions
- Suitable for insulated and non-insulated partitions
- Can be retrofitted
- No mechanical fixings required
- Robust galvanised steel shell
- Performance unaffected by weathering (Type X Durability)
Building Regulations impose limitations on all pipes passing through fire compartment walls and floors. QRS Vent Duct Slim Sleeves allow plastic ducts to meet the requirements of the Building Regulations. QRS Vent Duct Slim Sleeves have been tested according to BSEN 1366-3: 2009 where various plastic duct sizes have met insulation and integrity criteria for this standard for up to 2 hours.
The QRS Vent Duct Slim Sleeves consist of a flexible galvanised steel shell containing graphite based intumescent material.
They are manufactured to suit flat ducts of 110x54mm, 204x60mm and 220x90mm.
Tested to Type X durability which means the QRS Vent Duct Slim Sleeves can be installed in conditions exposed to weathering. QRS Vent Duct Slim Sleeves are expected to last the lifetime of the building.
QRS CE Marked Fire Sleeves are expected to last the lifetime of the building.Applications/Installation
The QRS Vent Duct Slim Sleeves should be placed around the ventilation duct, positioned centrally within the partition and should be flush or protrude from each face of the wall. The plasterboard should be cut to a tight fit around the QRS Vent Duct Slim Sleeves, and any gaps should be sealed with the GM Intumescent Acoustic Sealant.
around duct to ﬁt
QRS Sleeve (mm)
|QRS length (mm)||Fire
|QRS110/54SS||110 x 54||5||122 x 66||140||120 minutes|
|QRS204/60SS||204 x 60||5||216 x 72||140||90 minutes|
|QRS220/90SS||220 x 90||9||241 x 112||140||60 minutes|
Manuals and Documentation
Fitting Instructions - Fire Sleeve
URL for Fitting Instructions - Fire Sleeve copied to clipboard.
Ventilation Systems Catalogue
URL for Ventilation Systems Catalogue copied to clipboard.
Ducting Range - VS Catalogue Pages
URL for Ducting Range - VS Catalogue Pages copied to clipboard.
Fire Sleeve Slim - Catalogue Page
URL for Fire Sleeve Slim - Catalogue Page copied to clipboard.
Chiltern Report (IF11007)
URL for Chiltern Report (IF11007) copied to clipboard.
Chiltern Report (RF11067)
URL for Chiltern Report (RF11067) copied to clipboard.
Chiltern Report (BMT/FEI/F13139)
URL for Chiltern Report (BMT/FEI/F13139) copied to clipboard.
Chilton Report (BMTFEIF13139)
URL for Chilton Report (BMTFEIF13139) copied to clipboard.
Warrington Report (360670 Issue 2)
URL for Warrington Report (360670 Issue 2) copied to clipboard.