Fire Sleeves prevent the spread of fire where plastic pipes or plastic ducts penetrate fire compartment walls.
Features & Benefits
- CE Marked
- Tested to BSEN 1366-3: 2009
- Tested with Uncapped/Uncapped (U/U) duct configurations as required for ventilation ducts
- Up to 2 hour fire rating
- Suitable for masonry walls or plasterboard partitions
- Suitable for insulated and non-insulated partitions
- Can be retrofitted
- No mechanical fixings required
- Robust galvanised steel shell
- Performance unaffected by weathering (Type X Durability)
Building Regulations impose limitations on all pipes passing through fire compartment walls and floors. QRS Intumescent Fire Sleeves allow plastic ducts to meet the requirements of the Building Regulations. QRS Intumescent Fire Sleeves have been tested according to BSEN 1366-3: 2009 where various plastic duct sizes have met insulation and integrity criteria for this standard for up to 2 hours.
The QRS Intumescent Fire Sleeves consist of a flexible galvanised steel shell containing graphite based intumescent material.
They are manufactured to suit flat ducts of 110x54mm, 204x60mm, and 220x90mm. And round ducts with 100mm and 125mm overall diameter.
Tested to Type X durability which means the QRS Fire Sleeves can be installed in conditions exposed to weathering. QRS CE Marked Fire Sleeves are expected to last the lifetime of the building.
The QRS Intumescent Fire Sleeve should be placed around the ventilation duct, positioned centrally within the partition and should be flush or protrude from each face of the wall. The plasterboard should be cut to a tight fit around the QRS Intumescent Fire Sleeve, and any gaps should be sealed with the GM Intumescent Acoustic Sealant.
|Product Code||Duct Size (mm)||Space needed around duct to ﬁt QRS Sleeve (mm)||Recommended aperture
|QRS110/54||110 x 54||9||130 x 73||140||120 minutes|
|QRS205/60||204 x 60||9||225 x 80||180||120 minutes|
|QRS220/90||220 x 90||18||256 x 126||140||120 minutes|
* QRS130 and QRS110 are not currently CE Marked
Manuals and Documentation
Fitting Instructions - Fire Sleeve
URL for Fitting Instructions - Fire Sleeve copied to clipboard.
Ventilation Systems Catalogue
URL for Ventilation Systems Catalogue copied to clipboard.
Fire Sleeve - Catalogue Page
URL for Fire Sleeve - Catalogue Page copied to clipboard.
Chiltern Report (RF11067)
URL for Chiltern Report (RF11067) copied to clipboard.
Chiltern Report (BMT/FEI/F13139)
URL for Chiltern Report (BMT/FEI/F13139) copied to clipboard.
Chilton Report (BMTFEIF13139)
URL for Chilton Report (BMTFEIF13139) copied to clipboard.
Warrington Report (360670 Issue 2)
URL for Warrington Report (360670 Issue 2) copied to clipboard.