The independent EA testing, which measures airflow through the product, was conducted by the Building Research Establishment (BRE) and the acoustic testing by SRL Technical Services Ltd. The EA tests were carried out in accordance with UK Approved Document F (ADF) 2010 and the Scottish Technical Handbook 3.14.6 using the recognised test method to BS:EN 13141-1 clause 4. The independent testing substantiated the claimed performance data of the Titon Trimvent Select, SF Xtra and SFX Sound Attenuator trickle vents.
Greenwood’s 5000EA vent, known as Pyramid, and canopy is marketed in the UK as delivering 5000mm2 EA, yet the independent tests revealed the actual figure to be just over 4000mm2 EA. Similarly, the acoustic variant, 5000EAW.AC2, known as Pyracoust, only achieved 3634m2 EA. In addition, when these Greenwood products were tested for sound attenuation, the results show less attenuation than generally claimed.
No other products within the Greenwood portfolio were tested, as Titon’s research had only deemed that the products mentioned required further investigation.
Commenting on the testing, Tyson Anderson, Sales & Marketing Director at Titon said:
“Titon prides itself on the accuracy of its stated products performance and test results and believes that the market benefits from factually accurate data derived from recognised test procedures. This data will help manufacturers and specifiers ensure compliance with Building Regulations and that the provision for ventilation in a dwelling is correct for its occupants’ health and wellbeing. All our test reports are available for reference and can be explained if required.”
The following table details the findings of the independent tests as referenced in the press release:
* Other independent test house ** Titon internal test